Voted Best Answer
Feb 21, 2015 - 05:12 PM
The problem that you mentioned can be solved by two different ways
1- you can build a start up control in your control loop as you can see in this paper."A New Technology for HVDC Start-up and Operation Using VSC-HVDC System"
2- You can re-tune the controllers again