May 11, 2018 - 01:06 AM
2- Go to the main page --> Right Click on Transmission Segment --> Number of Conducotrs (6) & Termination Style (Remote Ends)
3- Add two remote ends . Right Click --> Name ( Same as Line Segment) & Number of Eq. Conductors (6) & Graphic Display (3 phase view)
4- Connect three phase versions of your sources and loads to the trasnmssion line terminal.
Please feel free to ask if you can not follow through.
May 11, 2018 - 11:29 PM
You can define two towers inside the transmission segment, with appropriate physical displacements according to the given geometry. For separate towers you can specify the conductor geometry as well as number of conductors/ bundle.If both ac circuits are arranged horizontally or vertically, you can choose any three conductor vertical/ horizontal tower cross section.
However, for a more complex phase arrangement, you can define 6 towers inside one transmission segment and define appropriate physical locations for them.