VSC hvdc, PSCAD
The case has some problems. For a start your PLLs are using degrees and set to track 60 Hz - The DQ0 transform blocks are expecting Radians. But that is not the only problem. I suggest looking at some VSC examples here: "https://hvdc.ca/knowledge-base/v:", and starting by getting one side of the link working, then the other, then connect them. Good luck.
Also, for a 10 kHz switching frequency you probably want to use a simulation time step of 10 micro seconds or less (not the default 50).
Add New Comment
Do you have the same question?
Follow this Question
This question has not yet been answered.
© 2013 Manitoba HVDC Research Centre · A Division of Manitoba Hydro International Ltd.