I am copying the email response sent by one of our transmission line experts to the customer so that we can all learn.
For a single cable, eliminate all outer layers of cable ( sheath, armour etc). This can be done by enabling conductor elimination for all layers as follows.
In the OUTPUT page, you can see the RXB data (Z=R+Xj, Y=jB)
SERIES IMPEDANCE MATRIX (Z) [ohms/m]:
SHUNT ADMITTANCE MATRIX (Y) [mhos/m]:
For two dc cables, eliminate all conductive layers as described above and then solve cable. This will create 2*2 matrix. For RXB data for ground and conductor modes can be computed manually using transformation matrix described in help (see Modal Analysis in help).
Example case is attached containing single and two cables
Software Support & Development Specialist
Manitoba HVDC Research Centre
a division of Manitoba Hydro International Ltd.
211 Commerce Drive | Winnipeg, Manitoba, Canada R3P 1A3
T +1 204 989 1241 | F+ 1 204 989 1277
email@example.com | www.hvdc.ca | www.pscad.com